These Floating Floor Underfloor Heating Packs are the perfect solution if minimal build-up is required. The smaller packs are ideal for conservatories and extensions where the underfloor is an afterthought.
Wood Floor finish can be applied directly onto the system so long as it is a minimum of 14mm thick and is click or tongue and groove manufactured.
FREE DELIVERY INCLUDED.
Mapei Eco 380 is our product of choice for bonding the panels to the subfloor – please check the product application. You may also want the primer to prep for the bonding product.
Floating Floor Underfloor Heating Packs Content
Please select the pack size required for actual content.
- 16mm Pipe – As Required
- Single Loop Control Pack or Manifold and Pump Set
- Reducers and/or 16mm Compression Couplings- As Required
- Bend Supports- As Required
- 1200 x 600 x 25mm Foiled Insulation Panels- As Required
- Foil Tape – As Required
For Controls please visit our – Temperature Controls.
- 25mm Thick
- Overall Dimension 1200mm x 600mm x 25mm
- Heat Output @ 50°C MWT = 80 W/m2
- Heat Output @ 40°C MWT = 55 W/m2
- Compressive Strength* (kPa) – 150 at 10% compression
- 100 Micron Aluminium Foil
Please contact the office if you wish for a quote for a different grade or thickness via [email protected].
The image is an illustration only, we may supply kits with either a Wilo or Grundfos pump. if you have a preference please leave a note and we will do our best to accommodate. Our manifolds are high-quality Manufactured Stainless Steel.
Tile, Laminate, and carpet flooring cannot be installed directly to these panels – a minimum of 18mm T & G Chipboard must be applied to the top of this. Engineer Wood flooring can be installed directly on top of the panels so long as both the following specifications are met.
- Minimum of 14mm depth
- Tongue groove or click
Frequently Asked Questions
Q. Can you have underfloor heating on a floating floor?
A. Floating floor systems are used where heating is to be installed over concrete floors. A Dry floor finish is necessary not a wet screed.
Q. What is the thinnest underfloor heating?
A. We have this system in 20mm and 25mm thickness. using a 16mm pipe @150mm centers.
Q. Is laminate flooring suitable for underfloor heating?
A. Yes, so long as there is a thermal break using a minimum of 18mm thickness.
Q. What Flooring is not suitable for underfloor heating?
A. Never use natural wood flooring with underfloor because it is not solid or stable enough to deal with the changes in temperature. Serious damage can be caused if installed directly onto a floating floor system.